DC0079 OFGEM Aproval
OFGEM have recently approved a proposed update to the DC0079 Distibution Code.
The modifications made to the Distribution Code, and Engineering Recommendation G59 are in relation to ensure that all existing embedded generators make changes to comply with the following:
That where rate of change of frequency (RoCoF) protection relays are used, as part of Loss of Mains protection, the applied setting should be 1Hzs-1 with a definite time delay of 500ms.
That vector shift protection technique should be removed where it is in use as Loss of Mains protection.
That existing Loss of Mains protection settings for type-tested generators need not be changed.
Any existing over-frequency setting relays still set at 50.5Hz should if possible be reset to 52.0Hz.
Of note above is the elevation of the over-frequency trip setting from 50.5Hz to 52Hz.
For details and more information, please download the following PDF document:
We will continue to share any updated information as and when it comes to light. Alternatively, enter your email address below to be kept up to date via email, or check directly at the ENA website here.
Our own DC0079 (Loss of Mains) information section can be found here.
GDPR – As a business to business communication, this letter is outwith the scope of the General Data Protection Regulations. Aside from that, we are happy to let you know that we hold no details about you other than those that are freely and publicly available on the Renewables and CHP Register. We will not contact you again in relation to this project unless you actively respond to us and give us permission to do so. We will not pass your details onto anyone else without your permission. If you provide us with any additional information over and above that freely available on the internet, we will ensure those details are kept fully in accordance with the GDPR.
The Energy Networks Association have opened up the portal for registration to the Accelerated Loss
This attached PDF contains the recent modifications made to the Distribution Code, and Engineering
Please refer to our Terms and Conditions
Follow the link to this morings (15/4/15) Radio Orkney featuring our very own Director Bryan
Find us by searching Bryan J Rendall (Electrical) Ltd